Main range of productModicon Quantum automation platform product or component typeAC discrete output modules discrete output number32 Complementary group of channels4 groups of 8 channels supply frequency47...63 Hz maximum voltage drop1.5 V discrete output voltage20...253 V AC addressing requirement2 output words absolute maximum output300 Vrmsfor 10 s AC400 Vrms 1 cycle AC maximum load current16 A rms per module4 A rms per group0.88 mA 230 V off state leakage per output1 A rms 20...253 V per output surge current2.5 A during 1 ms dV/dt400 V/ms response time<= 0.5 ms at state 0 to state 1<= 0.5 ms at state 1 to state 0 protection typeInternal output protection by 4 A fuseInternal by RC filter power dissipation1.60 + (1.0 V x total module load current) markingCE local signallingBus communication is present (Active): 1 LED (green)External fault detected (F): 1 LED (red)Input status: 32 LEDs (green) bus current requirement320 mA module formatStandard product weight0.45 kg Environment protective treatmentConformal coating Humiseal 1A33 product certificationsCULFM Class 1 Division 2 standardsUL 508CSA C22.2 No 142 electromagnetic compatibilityElectrostatic discharge immunity test - test level: 4 kV (contact discharge) conforming to IEC 801-2Electrostatic discharge immunity test - test level: 8 kV (air discharge) conforming to IEC 801-2Susceptibility to electromagnetic fields - test level: 10 V/m (80...1000 MHz) conforming to IEC 801-3 ambient air temperature for operation0…60 °C ambient air temperature for storage-40…85 °C relative humidity95 % without condensation operating altitude<= 5000 m Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS Directive Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Documents & DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.