Main range of productModicon Quantum automation platform product or component typeVAC discrete input modules software nameConceptProWORX 32Unity Pro discrete input number16 Complementary group of channels16 addressing requirement1 input word discrete input voltage24 V AC input current12 mA at 57...63 Hz10.7 mA at 47...53 Hz voltage state 1 guaranteed16...30 V AC at 57...63 Hz18...30 V AC at 47...53 Hz voltage state 0 guaranteed0...6 V at 57...63 Hz0...5 V at 47...53 Hz input impedance2600 Ohm capacitive at 57...63 Hz3100 Ohm capacitive at 47...53 Hz network frequency limits47…63 Hz maximum leakage current1.9 mA absolute maximum input30 V continuous32 V 10 s50 V 1 cycle response time4.9...0.75 ms x line cycle Off-On7.3...12.3 ms On-Off isolation between channels1780 Vrms for 1 minute isolation between channels and bus1780 Vrms for 1 minute bus current requirement180 mA maximum power dissipation in W5.5 W local signallingBus communication is present (Active): 1 LED (green)External fault detected (F): 1 LED (red)Input status: 16 LEDs (green) markingCE module formatStandard product weight0.3 kg Environment standardsCSA C22.2 No 142UL 508 product certificationsCULFM Class 1 Division 2 resistance to electrostatic discharge4 kV contact conforming to IEC 801-28 kV on air conforming to IEC 801-2 resistance to electromagnetic fields10 V/m 80…2000 MHz conforming to IEC 801-3 ambient air temperature for operation0…60 °C ambient air temperature for storage-40…85 °C relative humidity95 % without condensation operating altitude<= 5000 m Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS Directive Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Documents & DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsMarine certificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.